- Last Updated: 24 March 2015
- Hits: 135
Hydrant flushing is scheduled to begin on April 13, 2015. We plan to follow the normal route which is posed onlne at flushing.topsfieldpublicworks.org
Flushing removes sediment from the water mains, identifies hydrants in need of repair and checks system fire flows. Customers will have rust colored or black water while the water mains are flushed and for a period afterwards. The work will be conducted on weeknights from 9 PM until 1 AM to minimize the disruption. We apologize for the inconvenience.
Manganese levels in areas being flushed will be higher than normal and may exceed levels described in the drinking water advisory issued in November 2013. Do not drink, cook or make formula with the discolored water. Avoid using hot water while the cold water is discolored. Doing so will allow sediment to accumulate in your hot water tank and will take longer for the hot water to clear.
- Last Updated: 17 April 2015
- Hits: 204
The Town of Topsfield is requesting qualifications for engineering services for the design and construction of a water treatment facility. RFQ documents will be available on April 8, 2015. Qualifications are due on May 6, 2015 at 10:00 AM at Town Hall. Click here to view the advertisement.
Firms that have requested RFQ documents:
- Weston & Sampson, Inc., Peabody, MA
- Green International Affiliates, Inc., Westford, MA
- Environmental Partners Group, Inc., Quincy, MA
- Surveying and Mapping Consultants, Inc., Braintree, MA
- Amory Engineers, P.C., Duxbury, MA
- CDM Smith, Inc., Boston, MA
- Stantec, Westford, MA
- Integrated Marketing Systems, San Diego, CA
- B+AC, LLC, Somerville, MA
- Tighe & Bond, Westfield, MA
- Beals & Thomas, Southborough, MA
- Beta Group, Inc., Lincoln, RI
- PEER Consultants, P.C., Burlington, MA
- GEOD Consulting, Burlington, MA
- AECOM, Wakefield, MA
- CDR/MAGUIRE, Milton, MA
- Nitsch Engineering, Boston, MA
- Fay, Spofford & Thorndike, Burlington, MA
- Wright-Pierce, Andover, MA
- Tata & Howard, Marlborough, MA
- Comprehensive Environmental, Inc., Marlborough, MA
Questions & Answers
1. Will the Town's hydraulic model be made available or will a model be built for the project?
- Last Updated: 27 March 2015
- Hits: 3979
We test our sources for total manganese on a monthly basis. The results of these tests will be posted on this page as they become available. All results are shown in micrograms per Liter unless otherwise noted. The value shown is the average for the month if multiple samples were taken.
Please review the public notice that was sent to our customers in November 2013 to see how these levels compare to guidance from MassDEP. Manganese levels typically decline as water moves futher away from the sources because it precipitates out of solution and coats the pipe walls. Although system levels are normally low (<300 micrograms per Liter) this level can easily be exceeded when sediment in water mains and home plumbing lines is disturbed.
A system map (14 MB) showing the test sites and water mains is available to help customers determine which sampling sites are closest to their homes.
- Last Updated: 08 April 2015
- Hits: 665
The Town recently hired Woodard & Curran to fill the role of Owner's Project Manager for the Water Treatment Plant Project. The Commonwealth of Massachusetts requires an OPM for building construction projects that exceed 1.5 million dollars. The initial schedule calls for the design and bidding to be completed ahead of the May 2016 Annual Town Meeting where the Town will be asked to appropriate construction funding. If approved the plant will open during the summer or fall of 2017.
January 2015 Update: Woodard & Curran is developing the Request for Qualifications for the design work and reviewing/updating the feasibility study.
April 2015 Update: The Request for Qualifications for design services was published. Qualifications are due by May 6, 2015.
- Last Updated: 20 November 2013
- Hits: 5103
Drinking Water Advisory - Important information about manganese in your drinking water
Manganese is a nutrient that is part of a healthy diet. Drinking water may naturally contain manganese and, when concentrations are greater than 50 micrograms per Liter (µg/L), the water may be discolored and taste bad. Over a lifetime, the United States Environmental Protection Agency (EPA) recommends that people drink water with manganese levels less than 300 µg/L and over the short term, EPA recommends that people limit their consumption of water with levels over 1,000 µg/L, primarily due to concerns about possible neurological effects. Children up to 1 year of age should not be given water with manganese over 300 µg/L nor should formula for infants be made with that water for longer than 10 days.
Both of our water sources have exceeded the 300 µg/L threshold within the last year. The most recent test results show our source located on Perkins Row contains 394 µg/L of manganese; levels have varied between 150 µg/L and 370 µg/L in 2013 with an average of 313 µg/L. The most recent test result for our source located on North Street contains 94 µg/L; levels have varied between 70 µg/L and 1,270 µg/L during 2013 with an average of 391 µg/L.
- Last Updated: 29 October 2013
- Hits: 2343
What is a cross connection? It's an actual or potential connection between a potable water line and any waste pipe, soil pipe, sewer, drain or other unapproved source. These connections pose a threat to public health by allowing contaminants to be siphoned or forced into the public drinking water system under certain hydraulic conditions.
In a residential setting, cross connections include submerged hoses, lawn irrigation systems, chemical spray applicators, connections to private wells, boilers, solar heating systems and fire sprinkler systems. These connections, if left unprotected, could introduce contaminants to the water system. Consumers play an important role in protecting public health by notifying the Water Department of any cross connections and helping to eliminate or properly protect the connection by installing a backflow prevention device.